let suppose we have one Main distribution board with incoming breaker TP 40A , having two motors 10 kw Each as a load...
according to motors we have two TP 20A breakers on outgoing of the Distribution board and one breaker of 20A TP for capacitor bank of (10KVAR) so we have total three outgoing breakers..
let suppose, i switch off the outgoing breakers for the motors... now only main breaker and one outgoing breaker for capacitor bank is switch on..
please tell me what will be the power factor on the power factor regulator at no load????